Weather Masters, Inc. provides plumbing, heating & Air Conditioning repair and installation services in Ajo, AZ and surrounding areas.
Check out what some of our customers are saying about Weather Masters, Inc.
for Ajo, AZ
PROBLEM: UNIT BLOWING LOW VOLT FUSES DIAGNOSIS: PERFORM LOW VOLTAGE SHORT AND FOUND NO SHORTS TO GROUND. DID FIND THE LOW VOLTAGE TO BE 22 V. THIS IS CAUSED FROM THE INCOMING VOLTAGE TO BE 210V.. I CHANGED THE SETTING TO 208 VOLTS TO INCREASE LOW VOLTS.. THIS SYSTEM IS NOW RUNNING FINE WITH NO ISSUES.. TESTED DEFROST CONTROL. TESTED FREON LEVELS AMP DRAWS AND RUN CAPACITORS.