Weather Masters, Inc. provides plumbing, heating & Air Conditioning repair and installation services in Florence, AZ and surrounding areas. Check out what some of our customers are saying about Weather Masters, Inc. Plumbing, Heating & Air Conditioning services.
for Florence, AZ
wo16331 UNIT WAS FOUND TO HAVE A LOW CHARGE. AFTER FURTHER INSPECTION, A LEAK WAS FOUND ON INDOOR COIL. WEATHER MASTERS RECOMMENDS TO REMOVE AND REPLACE THE INSIDE COIL. REPAIR: ---REMOVE AND REPLACE INDOOR COIL WITH OEM PARTS - REMOVE AND REPLACE BI FLOW FILTER DRIER. - PRESSURE TEST, EVACUATE AND RECHARE SYSTEM WITH NEW R410A FREON UP TO 10LBS. EVAP COIL AND TXV UNDER PART WARRANTY. UNIT IS NOW RUNNING IN COOLING. NO ISSUES. 21 DEGREE TEMPERATURE SPLIT
wo16331 PROBLEM: WHEN UNIT IS TURNED OFF IN HEATING OR COOLING, OUTSIDE UNIT MAKES UNUSUAL NOISE. DIAGNOSIS: UNIT WAS INSPECTED AND WAS FOUND TO HAVE A LOW CHARGE. AFTER FURTHER INSPECTION OF THE INSIDE COIL, A LEAK WAS FOUND ON THE COIL. WEATHER MASTERS RECOMMENDS REPLACEMENT OF THE INSIDE COIL TO INSURE THE SYSTEM DOES NOT MALFUNCTION DUE TO LOW CHARGE.