Goodyear, AZ — Plumbing, Heating and Air Conditioning Service
Weather Masters, Inc. provides plumbing, heating & Air Conditioning repair and installation services in Goodyear, AZ and surrounding areas.
Check out what some of our customers are saying about Weather Masters, Inc.
for Goodyear, AZ
WO 15993 Problem: a/c not working. Thermostat wonâ€™t turn on Diagnosis: AN ELECTRICAL DIAGNOSIS OF THR SYSTEM. I WAS ABLE TO DETERMINE THAT THE UNIT HAS A FAULTY DOOR PANEL SAFTY SWITCH. THIS IS NOT ALLOWING CORRECT 120V TO THE FURNACE. I WAS ABLE TO BY PASS THE SWITCH FOR NOW BUT TO NEET SAFTY CODE FOR THE FURNACE. WEATHER MASTERS WILL NEED TO RETURN AND INSTALL A NEW DOOR SWITCH. THERMOSTAT IS INTERMITTENTLY CHANGING TEMPERATURES. RECOMMEND NEW THERMOSTAT. REPAIR: REPLACED BROKEN DOOR SWITCH AND REPLACED THERMOSTAT WITH HONEYWELL 8000. PERFORMED SYSTEM TEST, SEQUENCE OF OPERATION. TEST SUCCESSFUL. UNIT IS OPERATING NORMAL AT THIS TIME.
Need to install the right timer switch. Need to order. 12-7-18 - installed correct timer switch. home owner is now happy and has no other issues.
REPLACE INLINE PROGRAMMABLE LAUNDRY RM FAN OFFICE NEEDS TO BILL