Mesa, AZ — Plumbing, Heating and Air Conditioning Service
Weather Masters, Inc. provides plumbing, heating & Air Conditioning repair and installation services in Mesa, AZ and surrounding areas.
Check out what some of our customers are saying about Weather Masters, Inc.
for Mesa, AZ
Joe - Mesa, AZ
I would recommend to my friends
Claudia - Mesa, AZ
Chris did an excellent job, as usual.
Placone - Mesa, AZ
Amy - Mesa, AZ
We got several price quotes on our air conditioning but Weather Masters was the only one who gave us different options. They came right on time and did a fantastic job. Our home was left clean and the workers were friendly.
Crabtree - Mesa, AZ
Informative and trust worthy
Kolafa - Mesa, AZ
Williams. Myron - Mesa, AZ
Carpenter - Mesa, AZ
Jason was detailed, thorough, and professional in performing the biannual inspections on our AC units. He was right on time for the appointment and didn't waste any time during the inspection process.
Prompt knowledgeable service with great prices!
Lee - Mesa, AZ
This company is the finest in the valley! They provide all around quality service and very reasonable pricing. Give them a try, you won't be sorry.
Very good, as always
Willig - Mesa, AZ
Great Service !
Hoff - Mesa, AZ
Right on time, very efficient and pleasant. Great price !
Black - Mesa, AZ
McLellan - Mesa, AZ
The service man was clean and curtious
HVAC Go To Contractors in AZ
Dunlap - Mesa, AZ
I am a Commercial Property Manager working out of our corporate office in California. When I need HVAC service or a new unit, Weather Masters is who I can trust to do our serivce. They have a competent staff to answer any questions too. I appreciate how they understand the importance of maintaining our systems as long as possible before we make the investment to replace. Great all round company to work with.
Long - Mesa, AZ
Taxin - Mesa, AZ
Thank you for your prompt service.
Simpson - Mesa, AZ
Budwill - Mesa, AZ
Couldn’t be happier!
Simpson - Mesa, AZ
Everyone has been so professional and kind to work with. Wonderful company that I will highly recommend to everyone I know.
Great Service & Price!
Green - Mesa, AZ
Chris explained everything to me as he went along and let me see the damaged part that caused all the trouble. He really knows his stuff! He also explained the Membership deal and I joined right away. Great discounts have already started!
Scott - Mesa, AZ
Polite, very thorough good experience.
Great service, pleasant technician!
Long - Mesa, AZ
Cibella - Mesa, AZ
Very great job. Both technicians could hear the problem, got it diagnosed and fixed. Fantastic job. go one better 6 stars. You guys rocked it. Thank you so much. Now I an get some sleep.
Response from Weather Masters, Inc.:
We appericate your business!! Glad you able to sleep at night!!!
night and day AC unit.
Cibella - Mesa, AZ
Technician as nice and knows his job. But this unit had gotten very noisy that's why I call him back out. in the past 2 weeks now it more. Very noisy. It wakes me up 3-4 times a nite. I had some one come out and look at it. They said it is 'surging' and is not right.
Response from Weather Masters, Inc.:
Thank you for your feedback we will be out to look at the problem.
Gadberry - Mesa, AZ
The service was great and Chris was awesome to work with.
Gonzales - Mesa, AZ
Perform service call. Blank thermostat.
Provide estimate on new HVAC system.
Weather Masters will be performing a complimentary 6 month 37pt inspection after a complete HVAC system replacement!
Need a training on Thermostats
Replace condenser coil filter drier and do inspection of unit
Replacing condenser coil filter drier and inspection of system
Replacing a condenser coil Bi Flow Liquid Line Filter Drier perform pressure test Also do an inspection of the unit
Working up a bid for an install
SYSTEM DIAGNOSIS ON 12.5 TON COMMERCIAL ROOFTOP PACKAGE HEAT PUMP.
Inspection | coil cleanings
Split HP A’c unit / doing maintenance
Perform no cool service call. System diagnosis.
No cool service call on two commercial rooftop package units.
Checking out 7.5 ton commercial package unit thats not cooling well.
Today Weather Masters is performing a 37 point inspection on 3 residential split heat pump systems. Inspections include hosing down the outdoor coils. Flushing the condensate lines and checking Freon levels.
Heading out to Sun City Arizona to do a summer inspection
PROBLEM PMP VISIT 1 UNIT DAY AND NIGHT PHJ436000KTP0A1 C162697489 DIAGNOSIS 45/5 DUAL RUN CAPACITOR IS SHOWING WEAR BUT STILL WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME ALL MOTOR AMPS ARE WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME UNIT IS COOLING WITH A 20 DEGREE SPLIT ACROSS THE EVAPORATOR COIL NO RECOMMENDED REPAIRS AT THIS TIME TIGHTENED ALL ELECTRICAL CONNECTIONS HOSED OFF OUTDOOR COIL FLUSHED DRAIN
PROBLEM: UNIT NOT COOLING AND CONDENSATE LINE CLOGGED. DIAGNOSIS: NO ISSUES FOUND AT TIME OF INSPECTION. UNIT RUNNING NORMALLY IN COOLING WITH 18Â° TEMP SPLT CONDENSATE LINE DRAINING NORMALLY. WATER POURED DOWN MAIN DRAIN LINE AND DRAINED NORMALLY OUT SIDE OF HOUSE
PROBLEM 37 PT INSPECTION LENNOX A/H CBX25UH-048-230-10 171K27683 CONDENSER 14HPX-0480230-22 1917K16748 DIAGNOSIS UNIT IS 3LBS LOW ON R-410 REFRIGERANT 70/10 CAP IS WEAK FOR THE CONDENSER 20 MFD RUN CAPACITOR FOR THE INDOOR BLOWER MOTOR IS WEAK ALL THESE ISSUES WILL CAUSE PERMANENT INTERNAL DAMAGE TO THE MOTORS FOUND OIL IN THE DRAIN PAN/IF THE UNIT IS LOW AT NEXT CHECK WE WILL NEED TO DO A LEAK SEARCH FOR POSSIBLE LEAK ALL AMP FOR MOTORS ARE WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME TIGHTENED ALL ELECTRICAL CONNECTIONS HOSED OFF OUTDOOR COIL FLUSHED DRAIN A/H HAS LIMITED ACCESS FOR SERVICE/REPAIRS
PROBLEM: UNIT RUNNING IN HEATING DIAGNOSIS: NEW TSTAT INSTALLED NOT PROGRAMMED CORRECTLY FOR HEAT PUMP UNIT. TSTAT PROGRAMMED CORRECTLY AND UNIT RAN NORMALLY IN COOLING
PROBLEM INSPECTIONS @3 CARRIER ALL THREE UNITS ARE SHOWING WEAR DUE TO AGE AND USAGE MOTORS RUN CAPACITORS AND COILS SHOWING WEAR BUT OPERATING AT THIS NEEDED TO ADD CHARGE TO BOTH UPSTAIRS UNITS /THE DOWNSTAIRS UNIT CHARGE IS OK AT THIS ADD THREE 3LBS OF R-22 REFRIGERANT TO BOTH UPSTAIRS UNITS ALL 3 UNITS ARE COOLING WITH A 20 DEGREE SPLIT ACROSS THE EVAPORATOR COILS AT THIS TIME
PROBLEM NO COOL LOBBY UNIT YORK B3HP060A25A NOG8161746 DIAGNOSIS BLOWN LOW VOLT FUSE PREFORMED A LOW VOLTAGE TRACE AND FOUND DAMAGED WIRES IN THE SHEET METAL ELBOW REPLACED 6' LOW VOLTAGE WIRE UNIT IS COOLING AT THIS TIME
PROBLEM PMP VISIT 1 UNIT CARRIER 50JS-048---301-- 3205G41260 DIAGNOSIS UNIT IS COOLING WITH A 20 DEGREE SPLIT ACROSS THE COIL RUN CAPACITORS ARE SHOWING WEAR BUT STILL WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME ALL MOTOR AMPS ARE WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME UNIT IS SHOWING NORMAL WEAR DUE TO AGE AND USAGE NO RECOMMENDED REPAIRS AT THIS TIME TIGHTENED ALL ELECTRICAL CONNECTIONS HOSED OFF OUTDOOR COIL FLUSHED DRAIN
PROBLEM : A/C WONT TURN ON. DIAGNOSIS. FURNACE POWER CORD NOT SUPPLY POWER TO UNIT. REPLACED POWER CORD. THE UNIT FIRED UP. INSTALLED NEW HONEYWELL 6000 STAT.
PERFORMED 37 POINT INSPECTION ON ONE PACKAGE HEAT PUMP UNIT CHECKED AMP DRAW OF MOTORS TESTED RUN CAPACITORS TO BE WITHIN MANUFACTURERS RANGE VERIFIED TEMP SPLIT ACROSS COIL TIGHTENED ELECTRICAL CONNECTIONS CHECKED IN RUSH AMPS OF COMPRESSOR INSPECTED CONDITION OF UNIT UNIT RUNNING NORMALLY IN COOLING AT TIME OF INSPECTION. START ASSIST CAPACITOR INSTALLED AT TIME OF INSPECTION TO PROLONG LIFE OF COMPRESSOR. HONEYWELL 6000 PROGRAMMABLE THERMOSTAT INSTALLED AT TIME OF INSPECTION. WEATHER MASTERS RECOMMENDS FOLLOW UP INSPECTION IN FALL FOR HEATING SIDE OF SYSTEM.
PERFORMED PMP INSPECTION ON TWO SPLIT HEAT PUMP UNITS CHECKED AMP DRAWS OF MOTORS TESTED RUN CAPACITORS TO BE WITHIN MANUFACTURERS RANGE VERIFIED TEMP SPLIT ACROSS COILS CLEANED OUTDOOR COILS TIGHTENED ELECTRICAL CONNECTIONS CHECKED IN RUSH AMPS OF COMPRESSORS INSPECTED CONDITION OF UNITS BOTH UNITS RUNNING IN COOLING AT TIME OF INSPECTION. WEST UNIT HAS LOW MF 45/7.5 DUAL RUN CAPACITOR THAT WHILE UNIT IS RUNNING WHILE WEAK IS CAUSING PERMANENT INTERNAL DAMAGE TO MOTORS IT HELPS RUN. CAPACITOR WAS CHANGED AT TIME OF INSPECTION. WEATHER MASTERS RECOMMENDS INSTALLATION OF START ASSIST CAPACITORS TO HELP PROLONG LIFE OF COMPRESSORS. WEATHER MASTERS ALSO RECOMMENDS FOLLOW UP INSPECTION IN FALL FOR HEATING SIDE OF SYSTEM.
PROBLEM: A/C NOT COOLING. DIAGNOSIS: CONDENSER FAN MOTOR BEARINGS HAVE FAILED AND MOTOR SEIZED UP. REPAIR: REPLACED CONDENSER FAN MOTOR WITH NEW 2 SPEED OEM FACTORY MOTOR. REPLACED 45-5 DUAL RUN CAPACITOR WTH MOTOR. WARRANTY 1 YR PARTS. 30 DAYS LABOR. SERIAL E082421293 MODEL C4A648GKA200
PROBLEM PMP VISIT 2 UNITS DAY AND NIGHT CCA736GKA200 E171820103 DIAGNOSIS 40/5 DUAL RUN CAPACITOR IS SHOWING WEAR BUT STILL WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME /CAP MAY NEED TO BE REPLACED AT THE NEXT VISIT WITH THE LOW AMBIENT TEMPERATURES AND RAIN WE CAN'T PROPERLY VERIFY CHARGE AT THIS TIME /BUT IT IS WITHIN RANGE AT THIS TIME THE UNIT IS COOLING WITH NO RECOMMENDED REPAIRS AT THIS TIME LENNOX 12ACB36-5P 5801L 57263 DIAGNOSIS THIS UNIT IS SHOWING NORMAL WEAR DUE TO AGE AND USAGE RUN CAPACITORS ARE SHOWING WEAR BUT STILL WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME /CAPS MAY NEED TO BE REPLACED AT NEXT VISIT THIS UNIT IS COOLING WITH NO RECOMMENDED REPAIRS AT THIS TIME DUE TO THE AGE OF THE UNIT WE DON'T RECOMMEND ANY COSTLY REPAIRS TIGHTENED ALL ELECTRICAL CONNECTIONS HOSED OFF OUTDOOR COILS FLUSHED DRAINS
PROBLEM: NO COOL AFTER HOURS SERVICE CALL. DIAGNOSIS: BLOWN LOW VOLTAGE FUSE . DAUGHTER TRIPPED OVER THERMOSTAT WIRE CAUSING WIRE TO SHORT. REPAIR: RELACED LOW VOLTAGE FUSE. UNIT IS NOW RUNNING AND COOLING.
37 POINT INSPECTION DIAGNOSIS* PERFORMED 37 POINT INSPECTION ON EQUIPMENT CHECKED ELECTRICAL CONECTIONS, VERIFIED MOTOR AMP DRAWS COMPRESSOR AND OUTDOOR FAN COPACITER. INSPECTED SERVICE DISCONNECT VERIFIED SEQUENCE AND OPPERATION. INSPECTED SYSTEM PRESSURE, HOSED OFF OUTDOOR COIL, CHECKED AIR HANDLER SYSTEM IS OPPPERATING NORMAL AT THIS TIME. RECOMEND FOLLOW UP VISIT IN THE FALL.
REMOVE AND HAUL AWAY EXISTING H/P INSTALL NEW 14SEER DAY AND NIGHT 2.5 TON PCK H/P 25-20 BAR TYPE FILTER GRILL NEW SHEET METAL ELBOW AND ANGLE IRON STAND NEW DICONNECT AND WHIP AND FUSES CONNECT TO EXISTING ELECTRICAL CONNECT TO EXISTING DRAINS CONNECT TO EXISTING ROOF JACK 1YRS LABOR 10YR PARTS AND COMPRESSOR WEATHER MASTERS IS NOT RESPONSIBLE FOR DRYWALL /PAINT REPAIRS
CHECK AIR FLOW TO BED RM RECOMMEND REPLACING STAMP FACE REGISTERS WITH OBD STYLE
WEATHER MASTERS PROPOSES TO REPLACE EVAP CASE AND COIL DUE TO CURRENT COIL LEAKING AND IS OBSOLETE. 410A REFRIGERANT WILL BE ADDED BACK INTO SYSTEM. EVAP COIL INCLUDES A FILTER DRIER
WEATHER MASTERS PROPOSES TO: - DISCONNECT ROOFTOP PACKAGE UNIT FROM EXISTING ELBOW AND ROOFJACK. - INSTALL NEW ROOFTOP ELBOW AND ROOFJACK WITH NEW SUPPLY AND RETURN DROPS. - ENLARGE SUPPLY DUCT FROM 14 INCH TO 16 INCH R6 FLEX. ADD ADDITIONAL SUPPLY TRUNK TO 3 BEDROOMS WITH 14 INCH R6 FLEX. ADAPT NEW SUPPLY TRUNK LINES TO EXISTING SUPPLY BRANCH DUCTS USING TEE Y CONNECTIONS. - REMOVE 14 IN RETURN DUCT FROM EXISTING LOCATION AND CAP OFF. - CUT IN NEW 30X20 RETURN AIR CAN IN MAIN HALLWAY. - CUT IN NEW 20X20 RETURN AIR CAN IN MASTER BEDROOM. - ADAPT NEW RETURN CANS TO NEW RETURN DROPS WITH 18 AND 14 INCH R6 FLEXABLE DUCT. R6 - INSTALL NEW ECOBEE WIFI THERMOSTAT WITH 3 SENSORS TO ENSURE EVEN TEMPATURE THRUOUT THE HOME. - RECONNECT EXISTING 4 TON ROOFTOP PACKAGE HEAT PUMP TO NEW ROOTOP ELBOW AND JACK. - RECONNECT ELECTRICAL AND CONDENSATE. - PERFORM SYSTEM TEST TO ENSURE PROPER AIRFLOW. NOTE: WEATHER MASTERS WILL NEED ENLARGE THE ROOF OPENINGS TO INSTALL NEW ROOFJACK AND ELBOW. WEATHE
WEATHER MASTERS PROPOSES TO: - REMOVE AND HAUL AWAY EXISTING ROOFTOP PACKAGE HEAT PUMP. - INSTALL NEW 7.5 TON DAY & NIGHT ROOFTOP COMMERCIAL PACKAGE UNIT. 460V 3PH. -INSTALL NEW FUSED SERVICE DISCONNECT ELECTRICAL WHIP. -INSTALL (2) NEW ECOBEE THERMOSTAT W/ REMOTE SENSOR. ADDED ON A 2ND ECOBEE $350.00 WARRANTY- 1 YR PARTS, 5 YR COMPRESSOR, 1 YR LABOR PRICE INCLUDES ALL LABOR, MATERIAL, AND CRANE TO COMPLETE THE JOB.
Weather Masters successfully completed a 37 point inspection on 2 units - Weather Masters tightened all electrical fittings - Checked all Freon levels and pressures - Checked amperage of indoor and outdoor motor. Working at intended amperage -Ensured run capacitor is running with proper MFD's and is not leaking - Subcool is 15 and 12 -Examined indoor and outdoor coil. -Outdoor coil was cleaned with water -Temperature split is normal -Thermostat is working as should -Customer regularly changes filter so it is clean -Customer says unit is working well At this time, the systems are running normally
Weather Masters successfully completed a 37 point inspection on 2 units - weather Masters tightened all electrical fittings - checked all Freon levels and pressures - checked amperage of indoor and outdoor motor. Working at intended anprage -Ensured run capacitor is running with proper MFD's and is not leaking - subcool is 15 and 12 -examined indoor and outdoor coil. Outdoor coil was cleaned with water -temperature split is normal -thermostat is working as should -customer regularly changes filter so it is clean -customer says unit is working well At this time, the systems are running normally
PROBLEM: MINI SPLIT IN SERVER ROOM NOT COOLING. DIAGNOSIS: SYSTEM WAS LOCKED OUT ON HIGH DISCHARGE TEMPATURE LINE. THIS IS A RESULT OF A FREON LEAK LOCATED AT THE FLAIR CONNECTIONS. REPAIR: RECOVERED EXISTING R410 FREON. REPLACED THE FLAIRED CONNECTIONS. PRESSURE TESTED THE SYSTEM. EVACUATED THE SYSTEM. RECHARGED THE SYSTEM WITH 3 LBS OF NEW R410A FREON. CLEANED UP ALL THE OIL ON THE OUTDOOR UNIT DUE TO THE FREON LEAK. CLEANED THE OUTDOOR COIL AS WELL. UNIT IS NOW COOLING JUST FINE WITH NO OTHER ISSUES. NOTE: THIS WAS A LEAK FROM INSTALL DAY ONE.
PROBLEM: SYSTEM NOT COOLING. INDOOR FAN COMES ON BUT CONDENSER DOES NOT. DIAGNOSIS: SYSTEM IS COMPLETELY OUT OF FREON DUE TO A LEAK IN THE EVAP COIL. RECOMMENDED REPAIR: REPLACE EVAP COIL AND FREON
PROBLEM CHECK CONDENSER COIL@2 GOODMAN M/N FADED DIAGNOSIS DAMAGED /BENT FINS WILL REDUCE THE EFFICIENCY OF THE UNIT AND CAUSE PERMANENT INTERNAL DAMAGE TO THE COMPRESSOR BECAUSE OF THE AGE AND CONDITION OF THESE CONDENSER COILS /TRYING TO COMB THEM WILL CAUSE MORE DAMAGE TO THE FINS DUE THE OVERALL CONDITION OF THESE UNITS WE RECOMMEND REPLACING BOTH UNITS
PROBLEM: A/C NOT COOLING. DIAGNOSIS: THE SYSTEM ROOFTOP PACKAGE HEAT PUMP HAS A BAD COMPRESSOR AND A RESTRICKED FREON CIRCIUT. DUE TO THE AGE OF THE SYSTEM WEATHER MASTERS RECOMMENDS REPLACING THE SYSTEM.
PERFORM CHECK CHARGE ON A/C . UNIT IS RUNNING NORMAL WITH NO ISSUES. FREON LEVELS LOOK FINE. AIR FLOW LOOKS FINE. REMOVED THE METAL PLATE BEHIND THE THERMOSTAT.
W/O 16726 PULL AND CHEMICALLY CLEAN BLOWER WHEEL CHEMICALLY CLEAN EVAPORATOR COIL CHEMICALLY CLEAN CONDENSER COIL REPLACE 18 HP 1100 RPM CONDENSER FAN MOTOR MADE ALL RECOMMENDED REPAIRS EXCEPT PULL AND CLEAN BLOWER WHEEL/ AFTER FURTHER EVALUATION I FOUND THAT THE WHEEL WAS NOT THAT DIRTY/THIS REPAIR IS NOT NEEDED AT THIS TIME
PROBLEM: SYSTEM NOT TURNING ON DIAGNOSIS: BAD FUSE ON INSIDE AIR HANDLER DISCONNE T REPAIR: REPLACED 60 AMP FUSE WITH NEW 60 AMP FUSE AT THIS TIME, THE SYSTEM IS NOW RUNNING NORMALLY
PROBLEM: A/C HAS A BAD BELT AND VERY DIRTY AIR FILTERS. REPAIR: REPLACED 4) 16X25X2 IN FILTERS. AND REPLACED A 4L33 BELT. UNIT IS NOW RUNNING WITH GOOD AIRFLOW
PROBLEM 37 PT INSPECTION GOETTL M/N FADED UNIT IS 45 YEARS OLD DIRTY BLOWER WHEEL AND BLOWER MOTOR DRAIN PAN IS FULL OF DEBRIS EVAPORATOR COIL IS DIRTY MOTORS ARE SHOWING HEAVY WEAR SHEET METAL ELBOW IS NOT SEALED/WATER WILL LEAK IN THE HOME DUE TO AGE AND CONDITION WE RECOMMEND REPLACING THE UNIT WE DON'T RECOMMEND ANY COSTLY REPAIRS ATTACHED ARE PICTURES WASHED OUT DOOR COIL
PROBLEM NO COOL DIAGNOSIS T-STAT FAILED REPAIRS REPLACED T_STAT/HONEYWELL 5000
PROBLEM: NOTHING TURNING ON EXCEPT THERMOSTAT DIAGNOSIS: BAD CAPACITOR. COMPLETELY DEAD. REPAIR: REPLACE CAPACITOR THE SYSTEM IS NOW RUNNING NORMALLY AT THIS TIME