Weather Masters, Inc. provides plumbing, heating & Air Conditioning repair and installation services in Phoenix, AZ and surrounding areas. Check out what some of our customers are saying about Weather Masters, Inc. Plumbing, Heating & Air Conditioning services.
for Phoenix, AZ
Polite and professional
Black - Phoenix, AZ
Service guy was really late. Appointment was 12-3, but he arrived at 4. He apologized and provided reasonable explanation. Still, sounded to me like the company was at fault for his running late. They simply overbooked and he still had one more service call to go to when he was done with me at 5:00. Other than that, he able to do a check on my unit and I was glad to hear it was running ok and no need for any repairs. Service guy was very polite and professional. I didn’t understand the question on “convenience” listed below so I didn’t answer.
Kurt - Phoenix, AZ
My experience was good. He should uo as expected and was very professional and appeared to know what he was doing. Most important he did not do a hard sell or try to pressure me into purchases I did not need. The service man did his job well and met all my expectations.
Jason was very knowledgeable and very polite I think him for his service thank him
Ron - Phoenix, AZ
Jason was very knowledgeable and very polite I think him for his service thank him
Excellent service and communication
Ryder - Phoenix, AZ
Very impressed with Jason's calibre of service, communication regarding recommended repair of defective part, general manner.
Keith is Great
Whitmore - Phoenix, AZ
Keith Harris is always professional, on time, knowledgeable & informative. I appreciate Keith & Weather Masters in general. Thank you.
Sailer - Phoenix, AZ
OUTSTANDING SERVICE EVERY TIME.
GZ - Phoenix, AZ
Keith at Weather Masters is a professional. He's knowledgeable and has excellent communication skills. Wouldn't have anyone else service our AC unit. Great Job Keith!!
Black - Phoenix, AZ
Keith and his colleague were extremely professional, very thorough with their explanations and generous with sharing their knowledge about tackling the tricky problems associated with the leak. Very happy customers here!
Chris where is nice knowledgeable professional
Green - Phoenix, AZ
Response from Weather Masters, Inc.:
Thank you for being such a loyal customer we appreciate your business
Green - Phoenix, AZ
Chris was and is very Knowledgeable very polite a great human being
PERFORMED 37 POINT INSPECTION ON ONE PACKAGE HEAT PUMP UNIT CHECKED AMP DRAW OF MOTORS TESTED RUN CAPACITORS TO BE WITHIN MANUFACTURERS RANGE VERIFIED TEMP SPLIT ACROSS COIL CHECKED IN RUSH AMP DRAW OF COMPRESSOR INSPECTED CONDITION OF UNIT UNIT RUNNING NORMALLY IN COOLING AT TIME OF INSPECTION. WEATHER MASTERS RECOMMENDS FOLLOW UP INSPECTION IN FALL FOR HEATING SIDE OF SYSTEM
PERFORMED PMP INSPECTION ON ONE PACKAGE HEAT PUMP UNIT CHECKED AMP DRAW OF MOTORS TESTED RUN CAPACITORS TO BE WITHIN MANUFACTURERS RANGE VERIFIED TEMP SPLIT ACROSS COIL TIGHTENED ELECTRICAL CONNECTIONS CHECKED IN RUSH AMPS OF COMPRESSOR INSPECTED CONDITION OF UNIT UNIT RUNNING NORMALLY IN COOLING AT TIME OF INSPECTION. WEATHER MASTERS RECOMMENDS INSTALLATION OF START ASSIST CAPACITOR TO HELP PROLONG LIFE OF COMPRESSOR AND FOLLOW UP INSPECTION IN FALL FOR HEATING SIDE OF SYSTEM
PROBLEM PMP VISIT 1 UNIT GOODMAN GSX160481FC DIAGNOSIS 45/5 DUAL RUN CAPACITOR IS WEAK /RECOMMEND REPLACING THE CAP /THIS ALLOWS INTERNAL DAMAGE TO THE MOTORS UNIT IS 1LBS LOW ON REFRIGERANT /410/THIS CAN ALLOW THE COMPRESSOR TO GET HOT/RECOMMEND ADDING REFRIGERANT ALL AMPS ARE WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME UNIT IS SHOWING NORMAL WEAR DUE FLUSHED DRAIN TIGHTENED ALL ELECTRICAL CONNECTIONS HOSED OFF OUTDOOR COIL REPAIRS REPLACED 45 /5DUAL ADDED 1LBS 410 REFRIGERANT
PERFORMED PMP INSPECTION ON ONE SPLIT HEAT PUMP UNIT CHECKED AMP DRAW OF MOTORS TESTED RUN CAPACITORS TO BE WITHIN MANUFACTURERS RANGE VERIFIED TEMP SPLIT ACROSS COIL CHECKED IN RUSH AMPS OF COMPRESSOR TIGHTENED ELECTRICAL CONNECTIONS INSPECTED CONDITION OF UNIT UNIT RUNNING NORMALLY IN COOLING AT TIME OF INSPECTION. WEATHER MASTERS RECOMMENDS FOLLOW UP INSPECTION IN FALL FOR HEATING SIDE OF SYSTEM
WEATHER MASTERS PROPOSES TO: INSTALL NEW WHITE RODGERS COOLER CONTROL KIT. INCLUDES RUNNING A THERMOSTAT WIRE FROM THE COOLER TO THE INTERIOR WALL. COOLER TURNS ON AND OFF . PUMP WORKS FINE . NO OTHER ISSUES WITH THIS COOLER AT THIS TIME .
-REMOVE AND REPLACE 1 IN PILLOW BLOCK BEARRINGS. -REPLACE 115V COOLER WATER PUMP.
WO17100 PROBLEM: FAN NOT TURNING ON. DIAGNOSIS: YORK ECM BLOWER MOTOR FAILING. MOTOR NEEDS REPLACED. NOTE: INDOOR COIL IS DIRTY. INSIDE THE HOME SMELLS LIKE A CAT LITTLE BOX REALLY BAD. RECOMMED LETTING THE HOMEOWNER KNOW SHES GOT MULTIPLE CATS AND SHES NOTE CLEANING UP AFTER THEM. MODEL B2HZ036A06A SERIAL N1C1879943 WEATHER MASTERS WILL FORWARD ESTIMATE FOR REPAIRS.
ESTIMATE FOR DUCT WORK AND EQUIPMENT
PROBLEM NO COOL #304 50HCQA06A2M6A0A2A0 2518C80668 UNIT IS LOW ON REFRIGERANT PARTS ON WILL CALL SIGLER GILBERT COIL TXV
WO16891 PROBLEM. A/C NOT COOLING. DIAGNOSIS. GOODMAN GAS PACKAGE ROOFTOP UNIT. UNIT RUNS IN COOLING. COMPRESSOR , OUTDOOR AND INDOOR FANS TURN ON. THE SYSTEM HAS TWO VERY DIRTY COILS. INDOOR AND OUTDOOR. I RECOMMND CLEANING THE INDOOR COILS TO ALLOW THE UNIT TO BREATH BETTER. THE CONDENSER FAN MOTOR BEARINGS ARE LOOSE. THIS MAY RESULT IN A NO COOL. WEATHER MATERS RECOMMENDS REPLACING THE MOTOR. THE INDOOR BLOWER MOTOR HAS LOOSE BEARINGS. THIS WILL RESULT IN A NO COOL. RECOMMEND REPLACING THE BLOWER MOTOR. REPAIR. WEATHER MASTERS PERFORMED A SYSTEM CLEANING ON THE INDOOR AND OUTDOOR COILS. AFTER COMPLETEING THE CLEANING , THE FREON PRESSURES AND AIR FLOW WERE NORMAL. NOTE: WEATHER MASTERS DOES NOT SERVICE, REPAIR OR REPLACE WINDOW STYLE A/C UNITS.
WEATHER MASTERS PERFORMED COOLER INSPECTIONS ON 6 COOLERS. 2 FOUR SIDED COMMERCIAL 4 RESIDENTIAL MASTER COOL SINGLE SIDED WEATHER MASTERS NEEDED TO INSTALL (5) 1/4 INCH WATER LINES UP TO 8 FT LONG. WEATHER MASTERS REPLACED 6 PUMP SCREAN BASKETS. WEATHER MASTERS REPLACED ONE 115V COOLER PUMP. WEATHER MASTERS WAS ABLE TO CLEAN OUT ALL 6 COOLERS REPLACE WATER LINE FLOAT VALVE. ADD SCALE TABS TO EACH COOLER. REPLACE 6 BELTS. VERIFY SEQUENCE OF OPPERATION ON ALL 6 COOLERS. TEST MOTOR AMP DRAWS VERIFY UNIT CONDTIONS. NOTE: ONE COOLER IS MISSING A PLASTIC WATER TUB PANEL. THIS UNIT IS NOT RUNNING AT THIS TIME UNTIL THE PANEL ARRIVES. WEATHER MASTERS WILL REPLACE THE PANEL AT NO CHARGE. ONE COOLER HAS A BAD BARRING THAT NEEDS REPLACED. THE COOLER IS CURRANTLY RUNNING BUT THE BARRING WILL SEIZE UP OVER TIME AND CAUSE MOTOR DAMAGE. WEATHER MASTERS WILL FORWARD ESTIMATE FOR REPAIR. ONE COOLER HAS A FAILED PUMP SO THE COOLER WILL NOT RUN UNTIL THE PUMP IS REPLACED. WEATHER MASTERS W
Wo16712 WEATHER MASTERS PROPOSES TO: -REMOVE AND REPLACE THE BLOWER MOTOR HOUSING, WHEELS AND MOTOR. --- -WEATHER MASTERS WILL VACUUM AND CLEAN AIR HANDLER CABINET, ELECTRICAL COMPARTMENT AND EVAP COIL. -WEATHER MASTERS WILL PERFORM SYSTEM INSPECTION AFTER THE EQUIPMENT IS CLEANED AND BLOWER MOTOR REPLACED. NOTE THAT AFTER THESE REPAIRS ARE MADE THEN THE SYSTEM CAN BE INSPECTED FOR ANY OTHER ISSUES ONLY SEEN DURING A RUNNING SYSTEM. WEATHER MASTER WILL QUOTE FUTURE REPAIRS IF NEEDED. NOTE: BLOWER MOTOR AND HOUSING ARE SPECIAL ORDER PARTS AND MAY TAKE 7-10 DAYS TO ARRIVE. PARTS WILL BE ORDERED WITH APPROVAL OF REPAIRS.
PROBLEM WO/16545 WATER LEAK GOODMAN CKL30-1G 0403690780 A/H 30HX6-240 DIAGNOSIS DRAIN PAN RUSTED AND FULL OF DEBRIS /HANGERS FOR THE PAN HAVE RUSTED AWAY/PAN AT A NEGATIVE PITCH COIL IS VERY DIRTY AND RUSTED BLOWER WHEEL IS VERY DIRTY COMPRESSOR AND BLOWER MOTOR MAY HAVE TAKEN INTERNAL DAMAGE I PREFORMED A ELECTRONIC LEAK SEARCH /COIL HAS POSSIBLE LEAK/WE WOULD NEED TO ADD DIE TO PIN POINT A LEAK DUE TO THE CONDITION OF THIS UNIT WEATHER MASTERS RECOMMENDS REPLACING THE SYSTEM WE WILL PROVIDE ESTIMATE FOR REPLACMENT SEE ATTACHED PHOTO'S UNIT IS NOT COOLING WELL I DISASSEMBLED REASSEMBLED THE A/H HANDLER FOR INSPECTION HUNG DRAIN PAN /THIS REPAIR IS A TEMPORARY FIX TO THE PROBLEM
Weather Masters successfully completed a 37 point inspection - weather Masters tightened all electrical fittings - checked all Freon levels and pressures - checked amperage of indoor and outdoor motor. Working at intended anprage -Ensured run capacitors are running with proper MFD's and is not leaking - subcool is 10 -examined indoor and outdoor coil. Outdoor coil was cleaned with water -temperature split is normal -thermostat is working as should -filter was changed for the customer -customer regularly changes filter so it is clean -customer says unit is working well At this time, the system is running normally.
PROBLEM: NO COOL DIAGNOSIS: LOW FREON CHARGE DUE TO A LEAKING INDOOR EVAP COIL. INDOOR COIL WILL NEED TO BE REPLACED AND THE SYSTEM RECHARGED WITH NEW FREON. 12LBS WEATHER MASTERS WILL FORWARD ESTIMATE FOR REPAIRS. WEATHER MASTERS RECOMMENDS NEW SYSTEM AND WILL FORWARD ESTIMATE UPON REQUEST.
PROBLEM: SYSTEM CONTINUOUSLY RUNS. HAS TO SHUT OFF AT THE BREAKER DIAGNOSIS: SYSTEM WAS WIRED INCORRECTLY AMD THE CONTROLLER IS BAD. RECOMMENDED REPAIR: SYSTEM WAS WIRED CORRECTLY AND A NEW CONTROLLER MUST BE ORDERED
WO16851 PULL AND CLEAN BLOWER WHEEL 4-26-19 WEATHER MASTERS WAS ABLE TO PULL AND REMOVE THE INDOOR BLOWER MOTOR AND WHEEL. WEATHER MASTERS CLEANED THE INDOOR BLOWER MOTOR TO ENSURE THE BEST BLOWER PERFORMANCE. THE UNIT IS NOW BLOWING AIR BETTER AND CLEANER.
WO16837 REPLACE EVAPORATOR COIL 4-26-19 BEFORE PERFORMING COIL REPLACEMENT. I WAS ABLE TO PINPOINT THE LOCATION OF THE FREON LEAK. IT IS IN FACT NOT LOCATED IN THE EVAP COIL BUT ON THE REVERSING VALVE. I WAS ABLE TO REPAIR THE LEAK TO PREVENT NEEDING TO REPLACE THE VALVE. THE SYSTEM WAS THEN PRESSURE TESTED, EVACUATED AND RECHARCHED WITH 6.7 LBS OF NEW R410A FREON. THE SYSTEM IS NOW COOLING WITH NO OTHER ISSUES.
PERFORM 37 PT INSPECTION ON 1 SYSTEM. DIAGNOSIS: UNIT IS RUNNING GREAT. ONLY A FEW YRS OLD. TESTED FREON LEVELS. MOTOR AMP DRAWS AND RUN CAPACITORS. HOSED OFF THE OUTDOOR COIL AND FLUSHED THE CONDENSATE LINE. WEATHER MASTERS HAS NO RECOMMENDED REPAIRS AT THIS TIME.
LAST PMP INSPECTION. SYSTEM IS RUNNING NORMAL WITH NO ISSUES. TIGHTEN ELECTRICAL CONNECTIONS. TESTED FREON LEVEL. MOTOR AMP DRAWS AND RUN CAPACITORS. UNIT IS ABOUT 2 YRS OLD OR LESS WITH NO ISSUES AT THIS TIME. RECOMMEND A FOLLOW UP VISIT IN THE FALL TO INSPECT HEATING. HOME OWNER AT THIS TIME DOES NOT WANT TO RENEW PMP CONTRACT. HE WANTS TO PAY FOR EACH INSPECTION AT TIME OF SERVICE.
PERFORMED 37 POINT INSPECTION ON ONE PACKAGE HEAT PUMP AND ONE SPLIT HEAT PUMP UNIT CHECKED AMP DRAWS OF MOTORS TESTED RUN CAPACITORS TO BE WITHIN MANUFACTURERS RATING VERIFIED TEMP SPLIT ACROSS COIL CLEANED OUTDOOR COIL TIGHTENED ELECTRICAL CONNECTIONS INSPECTED CONDITION OF UNITS EAST UNIT HAS LOW 40/5 MF RUN CAPACITOR CAUSING POSSIBLE INTERNAL DAMAGE TO OUTDOOR FAN MOTOR AND COMPRESSOR. IF CAPACITOR CONTINUES TO WEAKEN UNIT WILL NOT FUNCTION IN COOLING. BOTH UNITS RUNNING IN COOLING AT TIME OF INSPECTION.
INSTALLED CUSTOMER SUPPLIED SWAMP COOLER MOTOR OLD MOTOR WAS 120V BUT HAD 240V APPLIED TO IT BY RESIDENT DURING SELF INSTALLATION. WEATHER MASTERS DID NOT INSTALL WHOLE SYSTEM AND THEREFORE CAN NOT GUARANTEE ITS PERFORMANCE. NEW SWAMP COOLER MOTOR RUNNING NORMALLY AFTER INSTALLATION.
PROBLEM NO COOL CARRIER PH3ZNB030000AA-- 1311X94933 DIRTY FILTERS UNIT LOW ON REFRIGERANT /PREFORMED ELECTRONIC LEAK SEARCH AND FOUND A LEAK AT THE EVAPORATOR COIL INDOOR BLOWER WHEEL IS DIRTY COMPRESSOR HAS TAKEN PERMANENT INTERNAL DAMAGE THE EVAPORATOR COIL WILL NEED TO BE REPLACED WE ALSO RECOMMEND PULLING AND CLEANING THE BLOWER MOTOR /RUNNING THE MOTOR WITH A DIRTY WHEEL WILL CAUSE INTERNAL DAMAGE TO THE BLOWER MOTOR/COMPRESSOR AND REDUCE THE EFFICIENCY OF THE UNIT ATTACHED IS ESTIMATE FOR BOTH REPAIRS WE WILL DO FURTHER DIAGNOSTICS AFTER THE REPAIRS
WEATHER MASTERS PROPOSES TO: - REMOVE AND HAUL AWAY EXISTING AMERICAN STANDARD 5 TON ROOFTOP COMMERCIAL PACKAGE UNIT. 3 PHASE 208/230V - WEATHER MASTERS WILL INSTALL NEW AMERICAN STANDARD 5 TON COMMERCIAL ROOFTOP PACKAGE UNIT 208/230V 3 PHASE - WEATHER MASTERS WILL INSTALL NEW 3 PHASE FUSED SERVICE DISCONNECT AND 1 IN ELECTRICAL WHIP. - WEATHER MASTERS WILL RECONNECT CONDENSATE DRAIN LINE. - WEATHER MASTERS WILL RE-USE EXISTING ROOFTOP CURB. - WEATHER MASTERS WILL INSTALL NEW HONEYWELL 6000 PROGRAMABLE THERMOSTAT. WARRANTY- 1 YR PARTS, 5 YR COMPRESSOR 1 YR LABOR. PRICE INCLUDES ALL MATERIAL , CRANE AND LABOR TO COMPLETE THE JOB.
WEATHER MASTERS PROPOSES TO: - REMOVE AND HAUL AWAY EXISTING 5 TON GAS FURNACE A/C SYSTEM - INSTALL NEW 5 TON 14 SEER DAY & NIGHT STRAIGHT COOL A/C WITH FURNACE. - INSTALL NEW EMERGENCY CONDENSATE DRAIN PAN. - INSTALL NEW CONDENSATE FLOAT SAFTY SWITCH. - INSTALL NEW FLEXABLE FLU PIPE. - INSTALL NEW FLEXABLE GAS LINE AND BALL VALVE. - INSTALL NEW FUSED SERVICE DISCONNECT AND ELECTRICAL WHIP FOR OUTDOOR UNIT. - INSTALL NEW HONEYWELL 8000 TOUCHSCREEN WIFI THERMOSTAT. - INSTALL NEW 30X20 BAR TYPE RETURN AIR FILTER GRILL. WARRANTY - 10 YR PARTS, 10 YR COMPRESSOR , 1 YR LABOR , 20 YR HEAT EXCHANGER. OPTIONAL 10 YR LABOR WARRANTY $1013 NOTE- WEATHER MASTERS IS NOT RESPONSIBLE TO DRYWALL/PAINT REPAIR DUE TO ATTIC ACCESS ENLARGEMENT DURING EQUIPMENT CHANGE OUT. HOMEOWNER HAS DECLINED THE EXTENDED WARRANTY AT THIS THIS TIME. $1013.00