Weather Masters, Inc. provides plumbing, heating & Air Conditioning repair and installation services in San Tan Valley, AZ and surrounding areas. Check out what some of our customers are saying about Weather Masters, Inc. Plumbing, Heating & Air Conditioning services.
for San Tan Valley, AZ
Sanders - San Tan Valley, AZ
Keith came and stated that we needed a new unit. He said he would work up a quote and gave me a price. He then talked to my husband and the price was 10K more. He never emailed the actual quote. When he came the compressor was working and when he left the plug no longer worked. It also took a week for them to come out and assess the problem. Not a fan and will not recommend.
Schmidt - San Tan Valley, AZ
REPLACE GOODMAN 410 CONDENSER ONLY/REUSE EXISTING DICONNECT AND ELECTRICAL WHIP WEATHER MASTERS IS NOT RESPONSIBLE FOR THE OPERATION /CONDITION OF THE EXISTING FURNACE REPAIRS REPLACED 4TON GOODMAN CONDENSER AND 60 AMP DISCONNECT /ELECTRICAL WHIP /FUSES UNIT IS COOLING AT THIS TIME GOODMAN GSX140481 1903117404 1 YRS LABOR 10 YRS PARTS /COMPRESSOR
PROBLEM NO COOL UNIT IS LOW ON REFRIGERANT FOUND LEAK AT THE CONDENSER CUSTOMER WANTS TO REPLACE THE CONDENSER
PROBLEM: A/C NOT COOLING. DIAGNOSIS: UNIT IS RUNNING WITH VERY LITTLE FREON. SYSTEM IS A YORK GARDIAN UNIT THAT USES R407C FREON. I INSPECTED THE INDOOR AND OUTDOOR UNIT AND FOUND THE INDOOR COIL TO BE VERY RUSTED AND DIRTY. THE OUTDOOR CONDENSER HAS A MELTED AND BROKEN DISCONNECT CAUSED BY LOOSE WIRE CONNECTIONS. THE DISCONNECT WOULD NEED REPLACED TO RESTORE POWER TO THE OUTDOOR UNIT. WITH THE INDOOR COIL BEING AS OLD AS IT IS AND RUSTED OUT , THIS WILL BE THE MOST COMMON PLACE OF A FREON LEAK. DUE TO THE AGE AND CONDITION OF THE SYSTEM WEATHER MASTERS RECOMMENDS EQUIPMENT REPLACMENT.
PROBLEM NO COOL GOODMAN DIAGNOSIS UNIT IS LOW ON CHARGE PREFORMED ELECTRONIC LEAK SEARCH AND FOUND A LEAKS AT BOTH SERVICE VALVES AT THE CONDENSER RUNNING THE UNIT WITH A LOW CHARGE WILL CAUSE INTERNAL DAMAGE TO THE COMPRESSOR ADD 7LBS OF 410 REFRIGERANT AT DISCOUNTED COST ADDED DIE WITH NO RETURN TRIP IF WE NEED TO COME BACK THE NORMAL DIAGNOSTIC FEE WILL BE APPLIED TO THE CALL DUE TO THE AGE AND CONDITION OF THIS UNIT WEATHER MASTERS RECOMMENDS REPLACING IF COSTLY REPAIRS ARE NEEDED *PER CUSTOMER HE WILL CALL IF THE UNIT STOPS COOLING
PROBLEM PMP VISIT 1 UNIT GOODMAN GMS80604BNBC 1411091913 DIAGNOSIS VERIFIED SEQUENCE OF OPERATION IN THE HEATING MODE AND THE UNIT IS HEATING WITH MANUFACTURE SPECIFIED TEMPERATURE RISE ACROSS THE HEAT EXCHANGER TESTED ALL SAFTEY AND LIMIT SWITCHES /NO ISSUES AT THIS TIME CHECKED ALL MOTOR AMPS/ALL ARE WITHIN MANUFACTURE SPECIFICATIONS AT THIS TIME 20 MFD RUN CAPACITOR IS OK AT THIS TIME NO RECOMMENDED REPAIRS AT THIS TIME
Performed routine maintenance for the winter on Trane unit for a customer with a preventive maintenance agreement in San Tan Valley, Arizona.