Weather Masters, Inc. provides plumbing, heating & Air Conditioning repair and installation services in Sun City, AZ and surrounding areas.
Check out what some of our customers are saying about Weather Masters, Inc.
for Sun City, AZ
Ease of Mind, Competent Technician
Sydney - Sun City, AZ
Had my annual A/C check out. The technician (Jason) was friendly, knowledgeable and efficient. All systems are “go!” Recommend getting the plan for servicing. They contact you to schedule an appointment, you get a tech sent in an emergency and you receive a discount. A win all around.
Three unit a.c. pre-summer inspection installed two start assist capacitors to prolong life of compressors
WEATHER MASTERS PROPOSES TO: - REMOVE AND HAUL AWAY EXISTING 3.5 TON ROOFTOP PACKAGE UNIT. - WEATHER MASTERS WILL INSTALL NEW 3.5 TON 14 SEER DAY AND NIGHT ROOFTOP PACKAGE HEAT PUMP. - INSTALL NEW FUSED SERIVE DISCONNECT AND ELECTRICAL WHIP. - INSTALL NEW HONEYWELL 6000 PROGRAMABLE THERMOSTAT. - INSTALL NEW 25X20 BAR TYPE RETURN AIR GRILL. - INSTALL NEW SIDE BY SIDE ROOFTOP ELBOW - INSTALL NEW REDWOOD UNIT SUPPORTS. WARRANTY- 10 YR PARTS, 10 YR COMPRESSOR, 1 YR LABOR. PRICE INCLUDES ALL LABOR , MATERIAL AND CRANE TO COMPLETE THE JOB.
PROVIDE EQUIPMENT REPLACMENT FOR 47 YR OLD GOETTLE UNIT.
WEATHER MASTERS WILL REMOVE AND REPLACE EVAPORATOR COIL AND CHARGE UNIT WITH NEW REFRIGERANT 4/2/19 WEATHER MASTERS REMOVED AND REPLACED EVAPORATOR COIL AND DRYER AND CHARGED UNIT WITH 13.75 LBS OF REFRIGERANT. DUE TO TIME OPERATING WITH LOW CHARGE FROM LEAK IT IS POSSIBLE COMPRESSOR HAS SUFFERED INTERNAL DAMAGE. WEATHER MASTERS RECOMMENDS REGULAR REPLACEMENT OF FILTERS TO ENSURE PROPER UNIT PERFORMANCE.
CHANGED 4 20X20X1 FILTERS
PROBLEM: UNIT NOT COOLING DIAGNOSIS: UNIT HAS LEAKING EVAPORATOR COIL. COIL MUST BE REMOVED AND REPLACED AND NEW R410A REFRIGERANT PUMPED IN TO FUNCTION IN COOLING
PROBLEM: UNIT MAKING RATTLING NOISE DIAGNOSIS: BLOWER WHEEL ON UNIT IS VERY OLD AND RUSTY CAUSING IT TO ROTATE IN AN UNBALANCED MANNER. I CALLED SIGLER WHO IS LOCATING THE PART WHICH IS RARE DUE TO AGE AS UNIT IS FROM 1986. IF NO OEM REPLACEMENT IS FOUND WEATHERMASTERS CAN REMOVE AND ATTEMPT TO FIND A SUITABLE REPLACEMENT WHEEL BUT WILL LEAVE THE IMPACTED AREA WITH NO HEAT OR A/C UNTIL FOUND.
1- REPLACE INDOOR BLOWER MOTOR WITH NEW MARS ECM BLOWER MOTOR. 2- REPLACE LIMIT SWITCHES. 3- REPLACE 3 PHSE SERVICE DISCONNECT. 60 AMP. 4 - REPLACE THERMOSTAT WITH HONEYWELL 5000 STAT. WEATHER MASTERS PERFORMED REPAIRS AND AT THIS TIME THE UNIT IS HEATING. TESTED NEW STAT IN COOLING AND HEATING AND WORKING FINE. NOTE: UNIT IS VERY OLD. WEATHER MASTERS MAKES NO GUARANTEE HOW LONG THE SYSTEM WILL RUN OR LAST DUE TO THE AGE AND OVERALL CONDITION.
REPLACE FILTERS, (4) 20X20X1 LOCATED ON THE ROOF.